Air Conditioner Condenser electrical additives
The fuse field or disconnect for the air conditioner condenser is required by using NEC code and have to be within reach of the condenser. The fuse box must have a way of protective the circuit for the condenser. notwithstanding the breaker in the primary panel, an air conditioner disconnect field desires to be fused or have a few sort of journey protection in case an electrical problem happens in the condenser with an electrical aspect. The protection must be sized consistent with the ampacity of the air conditioner as rated by way of the Mitsubishi Heat Pumps Auckland.
This information is to be had for unit ampacity and fuse length on the nameplate at the side of the condenser. The twine presenting the air conditioner unit need to be sized in step with NEC tables at 125% of RLA or Run Load Amps which is also rated at the unit plate with other records.
NEC and electric information
This records is available for unit ampacity and fuse length on the name plate on the aspect of the condenser. The wire providing the air conditioner unit must be sized in keeping with NEC tables at a hundred twenty five% of RLA or Run Load Amps which is likewise rated on the unit plate with different air conditioner nomenclature.
The fuse have to be sized no large than a hundred seventy five% of RLA of the unit and with exceptions can be raised to no greater than a maximum of 225% of RLA. This lets in for the fuses to have the ability to overcome the begin amps of the unit. begin amps are normally called LRA or Locked Rotor Amps which can a long way exceed the RLA for the primary cut up second while the unit begins.